Water Leaking Out Of The Heat Pump
Is it a leak or just condensation from normal operation? Here’s how to find out:
- Shut off your heat pump, leaving the pool pump running. In a couple of hours there should be a marked reduction in the amount of water around the bottom of the heat pump.
- Or, as an alternate method to check for a water leak, you can test the water draining out the base for the presence of the sanitizer you are using in your pool or spa. Use your water test kit, or a test strip, to check a sample of the water for chlorine or bromine. If the sample tests positive for sanitizer, call AquaCal for service at 727-823-5642. If the test is negative, the water is probably harmless condensation.
- NOTE: If you are using an Ionizer or Ozone Generator to produce sanitizer, this test method WILL NOT be effective.
Links of Interest
- Heat Pump Operating Cost Estimator
- Heat Pumps - 101
- Warranty Information
- Planned Maintenance
- Heat Pump - New Owner Basics
- Quick Start Guide
- Technical Support
- International Support
- Owner's Manuals
- Product Brochures
- AutoPilot Salt Chlorine Generators
- Sustainability Policy
- Thermolink Titanium Heat Exchanger
Recent Blog Posts
Connect with Us